Dual Electric Vehicle Energy Manager for Service Sizes up to 200A including Two NEMA 14-50 plugs
How It Works:
- The smart panel continuously monitors the real-time total power consumption of the home’s electrical panel.
- Detects instances when the total power consumption surpasses 80% of the main circuit breaker’s capacity and initiates a temporary de-energization of the EV charger.
- Automatically restores power to the EV charger when the total power consumption of the electrical panel remains below 80% of its capacity for a duration exceeding 15 minutes.
- Requires the availability of a double pole breaker slot in the panel.
- The EVETRIX panels MUST be installed and commissioned by a certified electrician based on National and Local Electrical codes otherwise the spare warranty will be voided.
- EvectriX panels operate at 40 amp or 50 amp, 208/240 VAC, which poses a significant electrical hazard. Always exercise extreme caution and follow proper safety protocols during installation. Hazard Voltage. Will cause severe injury or death.
- Before installation, ensure that the power supply to the charging system is completely shut off. Verify the absence of voltage using suitable testing equipment before starting any work.
- Cease utilization of the Panel promptly in the event of any defects, cracks, breakages, or damages. Under no circumstances should you attempt to alter, repair, or disassemble the EVETRIX panel. Kindly reach out to the manufacturer in case of any malfunctions or issues.
- Avoid installing the EVETRIX panel near flammable materials, explosives, fuels, chemical products, and vapors. Refrain from utilizing any cleaning solvents to clean the panel.
- Ensure that the control panel is properly grounded according to local electrical codes and regulations.
- Provide adequate ventilation for the control panel to prevent overheating. Avoid installing panels in enclosed spaces or near heat sources. During operation, it is essential to keep the panel door securely closed.
- Adhere strictly to the manufacturer’s installation guidelines for wiring, ensuring correct wire gauge, proper grounding, and appropriate circuit protection to handle the high voltage requirements.
- Implement appropriate isolation mechanisms, such as lockout/tagout procedures, to prevent accidental energization of the system during installation or maintenance.
- Encourage periodic inspections by certified electricians to identify any potential issues or wear and tear, ensuring the safe and efficient operation of the EV charging system.
NEX-PLUG-50/TWIN is an Electric Vehicle Energy Management System (EVEMS) smart panel featuring 2 EV charger output including two NEMA 14-50 plugs to connect a plugged-in EV charger.
These two plugs enable seamless connection of one or two electric vehicle chargers to an electrical panel, even in cases where the panel lacks the necessary capacity for a direct connection.
|40 × 40 × 21 cm
INPUT: 208/240 VAC
CONTROL VOLTAGE: 24 VDC 2A
WORKING TEMPERATURE：-20°C to +40°C
STORAGE TEMPERATURE： -20°C TO +40°C
OUTPUT: 2xNema 14-50 208/240 VAC
ENCLOSURE TYPE: NEMA 3R